Area of the floor of the compartment  [m2]      84.00
Height of the compartment              [m]       2.50
Initial temperature                    [K]     293.00
Initial pressure                      [Pa]  100000.00
Combustion Heat of fuel             [J/kg]  14000000.
Maximum timestep used by the solver    [s]      10.00
Timestep to print the results          [s]      10.00
Time of the end of the calculation     [s]    1800.00
********************************************
 
Type of the ceiling                    []          0
Area of the ceiling                  [m2]      84.00
Number of elements in the ceiling      []          7
Length/material of element n°  1,  [m]/[],      0.01/  1
Length/material of element n°  2,  [m]/[],      0.01/  1
Length/material of element n°  3,  [m]/[],      0.01/  1
Length/material of element n°  4,  [m]/[],      0.01/  1
Length/material of element n°  5,  [m]/[],      0.01/  1
Length/material of element n°  6,  [m]/[],      0.01/  1
Length/material of element n°  7,  [m]/[],      0.01/  1
 
Area of the floor                    [m2]      84.00
Number of elements in the ceiling      []          7
Length/material of element n°  1,  [m]/[],      0.01/  2
Length/material of element n°  2,  [m]/[],      0.01/  2
Length/material of element n°  3,  [m]/[],      0.01/  2
Length/material of element n°  4,  [m]/[],      0.01/  2
Length/material of element n°  5,  [m]/[],      0.01/  2
Length/material of element n°  6,  [m]/[],      0.01/  2
Length/material of element n°  7,  [m]/[],      0.01/  2
 
Length of the wall n°    1           [m2]       0.00
Number of elements in this wall        []          7
Length/material of element n°  1,  [m]/[],      0.01/  1
Length/material of element n°  2,  [m]/[],      0.01/  1
Length/material of element n°  3,  [m]/[],      0.01/  1
Length/material of element n°  4,  [m]/[],      0.01/  1
Length/material of element n°  5,  [m]/[],      0.01/  1
Length/material of element n°  6,  [m]/[],      0.01/  1
Length/material of element n°  7,  [m]/[],      0.01/  1
 
Length of the wall n°    2           [m2]       0.00
Number of elements in this wall        []          7
Length/material of element n°  1,  [m]/[],      0.01/  1
Length/material of element n°  2,  [m]/[],      0.01/  1
Length/material of element n°  3,  [m]/[],      0.01/  1
Length/material of element n°  4,  [m]/[],      0.01/  1
Length/material of element n°  5,  [m]/[],      0.01/  1
Length/material of element n°  6,  [m]/[],      0.01/  1
Length/material of element n°  7,  [m]/[],      0.01/  1
 
Length of the wall n°    3           [m2]       0.00
Number of elements in this wall        []          7
Length/material of element n°  1,  [m]/[],      0.01/  1
Length/material of element n°  2,  [m]/[],      0.01/  1
Length/material of element n°  3,  [m]/[],      0.01/  1
Length/material of element n°  4,  [m]/[],      0.01/  1
Length/material of element n°  5,  [m]/[],      0.01/  1
Length/material of element n°  6,  [m]/[],      0.01/  1
Length/material of element n°  7,  [m]/[],      0.01/  1
 
Length of the wall n°    4           [m2]       0.00
Number of elements in this wall        []          7
Length/material of element n°  1,  [m]/[],      0.01/  1
Length/material of element n°  2,  [m]/[],      0.01/  1
Length/material of element n°  3,  [m]/[],      0.01/  1
Length/material of element n°  4,  [m]/[],      0.01/  1
Length/material of element n°  5,  [m]/[],      0.01/  1
Length/material of element n°  6,  [m]/[],      0.01/  1
Length/material of element n°  7,  [m]/[],      0.01/  1
********************************************
Number of materials for partitions      []         2
Material N°    1
Density                           [kg/m3]     900.00
Conductivity                     [W/(mK)]       0.25
Specific heat                   [J/(kgK)]    1000.00
Relative emisivity, inside surface     []       0.80
Relative emisivity, outside surface    []       0.80
Convection coef., inside surf.  [W/(m2K)]      25.00
Convection coef., outside surf. [W/(m2K)]       9.00
Material N°    2
Density                           [kg/m3]     750.00
Conductivity                     [W/(mK)]       0.16
Specific heat                   [J/(kgK)]    9000.00
Relative emisivity, inside surface     []       0.80
Relative emisivity, outside surface    []       0.80
Convection coef., inside surf.  [W/(m2K)]      25.00
Convection coef., outside surf. [W/(m2K)]       9.00
********************************************
Number of openings                     []          3
Opening N°    1
Heigth of the sill of the opening     [m]       0.50
Heigth of the soffit of the opening   [m]       2.00
Width of the opening                  [m]       3.00
Contraction coef. (Bernoulli)          []       0.70
Opening N°    2
Heigth of the sill of the opening     [m]       0.50
Heigth of the soffit of the opening   [m]       2.00
Width of the opening                  [m]       3.00
Contraction coef. (Bernoulli)          []       0.70
Opening N°    3
Heigth of the sill of the opening     [m]       0.00
Heigth of the soffit of the opening   [m]       2.00
Width of the opening                  [m]       1.50
Contraction coef. (Bernoulli)          []       0.70
********************************************
The pyrolisis rate is defined point by point:
The number of points is   23
  time[s],RHR[W],pyrolisis rate[kg of wood/s],fire area [m²]
        0.        0.    0.0000    0.0000
        5.     7500.    0.0010    0.0010
       10.    30000.    0.0020    0.0050
       15.    67500.    0.0050    0.0110
       20.   120000.    0.0090    0.0200
       25.   187500.    0.0130    0.0310
       30.   270000.    0.0190    0.0450
       35.   367500.    0.0260    0.0610
       40.   480000.    0.0340    0.0800
       45.   607500.    0.0430    0.1010
       50.   750000.    0.0540    0.1250
       55.   907500.    0.0650    0.1510
       60.  1080000.    0.0770    0.1800
       65.  1267500.    0.0910    0.2110
       70.  1470000.    0.1050    0.2450
       75.  1687500.    0.1210    0.2810
       80.  1920000.    0.1370    0.3200
       85.  2167500.    0.1550    0.3610
       90.  2430000.    0.1740    0.4050
       95.  2707500.    0.1930    0.4510
      100.  3000000.    0.2140    0.5000
      400.  3000000.    0.2140    0.5000
     1800.        0.    0.0000    0.0000
********************************************
The number of forced vent is    0
********************************************
The number of horizontal vent group is             0
********************************************
The maximum fire area (   0.50m²) is lower than 25% of the floor area (  84.00m²). The fire load is localised.
********************************************
